for Johnstown, OH
Great service after the call back
Mike - Johnstown, OH
Just a small issue with the fans not shutting off once the technician left. After he came back, all is good.
Carl was was very fast and knowledgeable.
Brent - Johnstown, OH
Great service quick and on time
Rusk - Johnstown, OH
Charlyn - Johnstown, OH
Technician was awesome. Knowledgeable, helpful. Did an excellent job.
I completed a repair on an A/C. I installed a new primary control board for air handler. System operating at this time.
Performed tune up on ac, all tests were within manufacturing specs and system working properly upon departure.
Attempted to run system upon my arrival and found I had no refrigerant flow, checked the outdoor unit dual capacitor to see if it had failed and found it swollen up causing the terminals to break internally. Replaced capacitor, ran unit, checked temperature split and confirmed system operation. System is operating properly at this time
Performed a diagnostic service call for a furnace unit. Customer reported noise coming from around the evaporator coil. Upon inspection I found the TXV started to tap and spoke with Greg about what was happening. Greg explained to me that the noise was caused by refrigerant migration where refrigerant was moving to a colder area within the system.
Checked pressures on newly installed heat pump and found the superheat to be a bit high. Charged unit 1 lb R410A to take unit to a 21 degree superheat per my R410A calculator. IDT WB = 66 degrees, ODT = 75 degrees. Unit is operating as designed at this time. Unit was left operational upon my departure.
Replaced blower motor and tested its operation. Blower motor is operating properly at this time. Installers were finishing up AC install upon my departure.