for New Albany, OH
Tech wa fantas!
David - New Albany, OH
The technician was personable, knowledgeable, friendly and everything you would want from an associate representing your organization. Typically when you invite a technician into your home you always have a feeling that he will try to sell you something you don’t need, however nothing could be further from the truth. This guy was super friendly and knowledgeable. Made me feel at ease the moment we met in the driveway. I would recommend him to anyone else looking for any air-conditioning or heating repair.
Isiah was great
Todd - New Albany, OH
Clearly provided all options available.
Jacob was great!
Jan - New Albany, OH
Had problem after service visit and Jacob came back out on same day. Fixed and cleaned up water from condensation. AC unit now working better than before service.
Thanks for the convenient and quality service!
Laticia - New Albany, OH
Fan - New Albany, OH
Green - New Albany, OH
Surprised at how quickly he was done.
Andrew Doud - New Albany, OH
Arin Heinsekman - New Albany, OH
Max - New Albany, OH
Everything went great
GB - New Albany, OH
Tech was extremely thorough and eager to answer any questions
There is a water meter that is directly in front of filter rack, that makes it tough to remove and install filters, you would need to bend filter up and inch it in, Installed new filter for customer and showed customer how to remove and reinstall filter, also showed customer about installing filter in cabinet under blower as an alternative option, Customer would like us to see if there is anything that we can do to raise filter rack so it would be above water meter, There are photos attached to job, System operational at departure.
Diagnostic Service Call Service work performed: Customer states lines froze over evap coil is 35% restricted with dirt pressures 25/135psig supply temp in cooling 61 degrees return drop temp 70 air handler is 38 years old and outdoor unit was manufactured before 1999, I believe a 1992. unit holds over 9 lbs 11 ounces of R-22 system has a leak system needs anywhere from 2-4 lbs of freon customer wants to add freon and get estimates