for Gahanna, OH
Great check of my heat pump
Hal - Gahanna, OH
On time knowable and helpful tech no problems
Winter Heating Check Up
Greg - Gahanna, OH
on time, friendly, and our dog loves your tech
Carol - Gahanna, OH
Quick and Honest
Craig - Gahanna, OH
BI ANNUAL CHECK UP EVERY THING OK AND THEY ANSWERED ALL MY QUESTIONS
Hal - Gahanna, OH
Katrina - Gahanna, OH
Vincent - Gahanna, OH
All reps I met were friendly, courteous and customer oriented
I completed scheduled maintenance spring tune up on a Carrier air conditioner. I visually inspected the furnace. Checked voltage and amps. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating normally at this time.
I completed diagnostics and found the unit is low on refrigerant. Potential slow leak. I was authorized to add refrigerant. The unit is operating and is cooling as intended.
I performed a tune up and safety check on a Carrier 13 SEER 2 Ton Air Conditioner. I found no issues and the system was operating within manufacturer's specifications when I left.
I completed a diagnostic on a York gas furnace. Determined that the filter was dirty. Client to replace filter. Gas pressures were high. I adjusted the gas pressure to within manufacturer's specifications. Cycled and monitored the system. Operating normally at this time.
Return Service for a Goodman heat pump and electric furnace. I replaced the blower motor and capacitor. Cycled and monitored the system. Operating normally at this time.
Upon arrival air handler was not working or heating. Visually inspected air handler condition system was a little bit older found limit switches and relays on the inside of the air handler to be a little bit rusted normal wear and tear found blower motor had quite a bit of debris dust and dirt around the outside of the blower blower motor was not running checked power to the blowerHad power to the blower motor blower motor Windings are bad in the blower motor is not working blower motor will need to be replaced.