for Reynoldsburg, OH
Caleb - Reynoldsburg, OH
Great Service and Price!
JC - Reynoldsburg, OH
The installation of the new furnace and A.C. went very smoothly and the HVAC installers were knowledgeable and efficient.
Jcc - Reynoldsburg, OH
They were very efficient and knowledgeable in the installation of the AC and furnace. They came out this month to check and adjust the AC for the warmer months to come as part of the installation fee.
McConnell - Reynoldsburg, OH
Todd - Reynoldsburg, OH
Ben was our technician this morning to complete our cold season checkup as part of our maintenance contract. He was extremely polite and very professional. I am a technical person (not HVAC) and observed him while he worked. He took the time to answer my questions and explain the results. He did not push any products like some techs and we appreciate that. Based on this visit we will continue to use this company.
Scott - Reynoldsburg, OH
The technician was courteous and knowledgeable, he made repairs in a timely manner.
Michaele - Reynoldsburg, OH
We have had these folks for many years! They installed our current unit and do twice yearly check ups. They are always prompt, professional and the price is always fair. I would recommend them to anyone who wants good, quality ac/furnace/heat pump service. Their professionalism has made us long time customers and we will continue to use them!
Denise - Reynoldsburg, OH
The technician was quick to identify the problem and fix it quickly. I was really pleased with the speed of the remedy.
Nercy - Reynoldsburg, OH
Great service on a Saturday! Fixed me up and at a good price
Brian - Reynoldsburg, OH
I completed a diagnostic on a 2002 Rheem Air Conditioner. I tested the system and found the cpa reading at 43/3 out of 45/5, found the compressor was bad, tried to start the a/c and blew the breakers and fuse. Sent the customer an estimate for repair and replacement.
Upon arrival flames on furnace would kick on and the blower motor failed to follow, after further diagnostic discovered that we have high voltage going to blower and the motor is hot to the touch. B Blower needs replaced, Provided customer with repair and replacement options. Furnace not operational at departure.
I completed a diagnostic on a 2020 Carrier Gas Furnace. I determined that the drain is overflowing due to the humidifier running. Drain was cleared and condensate pump and tubing was ordered to correct issue. System was operational at time of departure.
I arrived to install a Honeywell smart thermostat that the customer already purchased. system was operational at time of departure.