for Powell, OH
Rachel - Powell, OH
Great and friendly service!!!
Upon arrival for callback on 2021 Five Star furnace, customer concerned about flashing yellow lights from unit. Found unit operating as intended, flashing light is heartbeat which is normal operation for this unit. Addressed customers other concerns. System operating as intended upon departure.
Upon arrival for tune up safety check on 2007 Payne furnace, turned thermostat up 5 degrees from inside temperature for a call for heat. Visually inspected furnace condition and operation. Furnace return air filter was dirty and installed back wards. Removed front cover of furnace inside was a little dusty and dirty but not bad considering the age of everything. Inducer motor was in good condition with a good amp draw per manufacture specification. Burners were a little dusty but still allowing gas to flow through the way they were designed to. All limits and switches were operating normal. Gas pressure was good. Blower motor was operating normal with a good amp draw. Blower Capacitor tested out of spec, notified customer and replaced it. Combustion efficiency was good at 82.3% efficient on combustion. Put cover back on furnace double checked operation. System running normal. Customer also purchased iWave Air Cleaner through us and I installed.
Upon arrival for tune up safety check on 2020 Carrier furnace, humidifier water shut off valve was off turned on and checked humidifier all is ok. Customer also had concerns about the iWave air purifier, checked and it was installed on EAC terminal went ahead and wired up to L1 and neutral, tested air purifier and it is all good. All other items checked out good within manufacture specs at this time. System operational at departure.