for Powell, OH
Rachel - Powell, OH
Great and friendly service!!!
Customer was not told to turn off AC unit. Evap coil frozen solid. Will return next day
Upon arrival system was off at thermostat, Turned to cool and set temp down, System kicked on operational, Tested dual capacitor on condenser it is 35/5 and it is reading low at 27.4/4.4 will need replacement Customer is not interested at this time, Condenser fan’s mounting bolts are broken and it is only being held by two bolts causing fan to vibrate, will eventually burn fan out, Condenser coil was dirty rinsed off with water,System operational at departure.