for Powell, OH
Rachel - Powell, OH
Great and friendly service!!!
I found inducer locked up, I was able to get it spinning and unit ran fine for 3 startups, inducer bearing sounds really rough, rust on inducer and gas valve, system is only two years old. Inducer and gas valve should be replaced. T will also need installed on intake to prevent possible future damage
Upon arrival system was off , turned on and cycled in both heat and cool, system is operational with no issues, Customer stated that he would like to set the t-stat to auto so it would automatically switch modes, Set t-stat to auto mode and noticed the t-stat is going blank and not functioning correctly, Replaced t-stat and installed a Honeywell T6 , Cycled system in both heat and cool, System operational at departure.