for New Albany, OH
Tech wa fantas!
David - New Albany, OH
The technician was personable, knowledgeable, friendly and everything you would want from an associate representing your organization. Typically when you invite a technician into your home you always have a feeling that he will try to sell you something you don’t need, however nothing could be further from the truth. This guy was super friendly and knowledgeable. Made me feel at ease the moment we met in the driveway. I would recommend him to anyone else looking for any air-conditioning or heating repair.
Isiah was great
Todd - New Albany, OH
Clearly provided all options available.
Jacob was great!
Jan - New Albany, OH
Had problem after service visit and Jacob came back out on same day. Fixed and cleaned up water from condensation. AC unit now working better than before service.
Thanks for the convenient and quality service!
Laticia - New Albany, OH
Fan - New Albany, OH
Green - New Albany, OH
Surprised at how quickly he was done.
Andrew Doud - New Albany, OH
Arin Heinsekman - New Albany, OH
Max - New Albany, OH
Everything went great
GB - New Albany, OH
Tech was extremely thorough and eager to answer any questions
Upon arrival I found the 2004 Rheem system not operational, After further diagnostic found low voltage fuse blown on board, replaced fuse furnace went through cycle and as soon as it would call for gas valve it would blow the fuse, gas valve is bad and needs replaced, System operational at departure.
Arrived on site to #4 open high limit. Limit is closed as should as well as all other safety devices Reset at mulex plug. The 2001 Trane Furnace back up and running. 124.5 degree supply temp and 72.5 return temp. 52 degree temp rise. Temp rise ok but recommend less restrictive filter. Furnace heating at departure but circuit board could fail at any time. Customer wants estimate to replace system
Customer just moved in and Tried to program stat so that she can control from her phone and then heat would not cycled. Found thermostat barley attached to wall. Screwed down and seated. Found no common hooked up. And wife seated at * terminal. Moved to common and wired in at board. Cycled hearing and cooling from stay no issue. Had customer control from phone with no issue
I am Performing our Five Star Tune-Up & Safety Check on a Gas Furnace. All readings were within manufacturer's specifications, unit operating properly at this time.