for Lewis Center, OH
I found the filter is dirty and needs replaced, the igniter is also reading high ohms and the plug is dry rotten and is very bridle and will need replaced. I found the blower motor is dirty and needs uninstalled cleaned and reinstalled, as well as the blower capacitor is rated at 7.5mfd and it's only showing 6.5 will also needs replaced, Recommend furnace replacement due to age and cost of repairs. System operational at departure.
Upon arrival for service call on 1995 Lennox Pulse furnace, we do not work on this type of system, it has a burned up blower motor. Provided customer with an estimate for furnace replacement and also waiving diagnostic fee. Customer will review and get back with us.
Upon arrival found 2004 Carrier system not operational, Was showing led code 21 gas valve failure, Reset system and ran through heat cycle, furnace operational normal for 20 minutes without any fault or errors, gas valve is intermittent and may fail again,