for Lewis Center, OH
Coil was iced over and leaking water,Need to replace blower motor with capacitor, did not have a 115v tps motor, will need to order motor and return to complete repairs, Customer wants to move forward with repairs. The 2012 Carrier System not operational at departure.
Upon arrival the 2019 Carrier system was operational, Took panel off on evap coil and noticed pan is holding water and is over flowing out of pan, Blew out drain line with nitrogen, water drained from pan, Wiped off access water on furnace, System operational at departure.
Tuneup on Bryant AC. All checks are good at this time.
upon arrival I found a Armstrong furnace was not operational, after further diagnostic discovered that the inducer motor is seized/bad and needs replaced, tech recommends replacing furnace due to age of furnace and cost of repairs, furnace not operational at departure.