for Hilliard, OH
Friendly, thorough service. Found the issue.
Brett - Hilliard, OH
Carl spent the time tracing a very hard-to-find short. He was able to narrow it down to wires against a pipe. I'm back in business.
Shazia - Hilliard, OH
Cathy - Hilliard, OH
Fantastic company, great service, Carl was very thorough, friendly, and professional!! We will definitely us them again!!
great service great Tech
Joe - Hilliard, OH
Carl the Tech. was on time ,neat appearance Very mannerly,well trained in his trade.
Upon arrival for callback on 2020 Five Star furnace, performed an electronic leak search and also with soap and bubbles. Located leak passed shut off valve at the first elbow. No other leaks. Took line apart from shut off valve to union. Redoped and reinstalled line. Turned gas back on cycled furnace in heat to get all air out of lines. Then performed electronic and also soap bubble leak search. No sign of any more leaks. System operational at departure.
I performed a tune up on a Lennox gas furnace. While performing the tune up, I found both the inducer motor capacitor as well as blower motor capacitor are out of spec. I recommended the customer replace both parts. The customer did not want to at this time. System is operational at departure.
Upon arrival for service call on 1999 Trane furnace, I performed combustion analysis test and the furnace passed the test. Tested flame sensor, pulled and cleaned flame sensor. Reinstalled and tested after cleaning . Furnace continued to operate as intended while tech was present. System operational at departure.
Performed tune-up on a Tempstar gas furnace. Found that filter was the wrong size and rust is forming at the tips of the burners. I removed, cleaned and reinstalled the flame sensor. Everything else was working properly.