for Hilliard, OH
Friendly, thorough service. Found the issue.
Brett - Hilliard, OH
Carl spent the time tracing a very hard-to-find short. He was able to narrow it down to wires against a pipe. I'm back in business.
Shazia - Hilliard, OH
Cathy - Hilliard, OH
Fantastic company, great service, Carl was very thorough, friendly, and professional!! We will definitely us them again!!
great service great Tech
Joe - Hilliard, OH
Carl the Tech. was on time ,neat appearance Very mannerly,well trained in his trade.
Upon arrival found condenser unit on the 1991 Carrier not operational, After further diagnostic discovered that the dual capacitor is bad and also the lead wire to the compressor was burned up, Replaced 50/5 dual capacitor and repaired bad lead wire to compressor, System kicked on, checked amp draw on compressor, compressor is over amping and that is why it burned up wires and will definitely happen again,
found furnace on upon arrival but Amanda a/c was not responding to call for cooling, I checked breaker in panel it was not tripped. I checked disconnect and he was not getting power to the load side, I changed out the fuses and unit came on. All operating as it should upon departure.
Upon arrival found the 2004 Trane system froze up, customer stated that no one told him to shut system off, Unable to perform diagnostic or leak search due to system froze up, Recommended not to run a/c and only run fan to move air, System not operational at departure.
Upon arrival found condensation drain line clogged, Took drain apart and cleared of all debris, also blew out with drain gun, Checked air filter and it was also clogged, removed filter to not risk freeze up, made customer aware he will replace filter today, System operational at departure.