for Granville, OH
Seth - Granville, OH
Prompt and helpful service
Matt - Granville, OH
Greg - Granville, OH
Great people to work with.
Repaired pair of 40 AMP buss fuse on Rheem AC. System cooling properly at departure.
Customer wanted a quote. Ac going in tomorrow
Water on floor and dripping into furnace Found joint on evap Pan cracked. Sealed with Pan sealant. Cleaned up water inside furnace. Customer unhappy with media filter rack(please see reminder). Preferably entire evaporator coil needs replaced with Pan. Looks like a manufacture joint defect on the Pan
Diagnostic Service Call on 2014 Carrier AC Unit. Service work performed: Found N COIL uncased. Found metal lip preventing proper air flow, cut metal lip off. Found AC unit grossly over charged. Removed refrigerant AC cooling well at departure