for Dublin, OH
Fast response and diagnosis.
John - Dublin, OH
Great tune-up service
Jenping - Dublin, OH
The technician arrived on time, performed AC check up and gave us a few tips on increasing AC performance. The service was professionally done. Will hire them again.
Arrived on time; finished in a few minutes.
Apple - Dublin, OH
John - Dublin, OH
Courteous inistallers, very responsive to our needs
Bob - Dublin, OH
Responded quickly on a very cold Sunday evening. Installation of our new furnace was next day! The guys were terrific and really cleaned up after themselves.
Tonya - Dublin, OH
He was efficient and professional and I like that he didn't try to sell me somethi,g that I didn't need.
Upon arrival for tune up safety check on 2020 Carrier furnace, I went through furnace tune up list, everything checked out normally per routine maintenance. System is working within manufacturers specifications. System heating properly upon departure.
I completed a diagnostic on a Carrier heat pump with an electric furnace. Upon arrival found that the heat pump was not operational. Determined that the unit is low on pressure. Performed an electronic leak search and found leak. Will need a return service to repair the leak. System is operational in auxiliary heat mode.
I completed a diagnostic on a Rheem furnace. Upon arrival found the evaporator coil extremely iced up. I determined that condenser was replaced a couple of years ago with an air conditioner and not a heat pump. Due to that if the thermostat is set to heat instead of emergency heat it will turn on the air conditioning unit. I explained this to the tenant and also contacted the landlord to give instructions. Cycled and monitored the system. Operating normally at this time.
I performed a diagnostic on a new gas furnace. Upon arrival furnace was not operational, showing led code 33, limit circuit fault. I checked filter and it is clogged/dirty, removed filter and made customer aware. I cycled system in heat and checked temp rise, and it was at 55 degrees on first stage. I checked gas pressure first stage was set to 1.91inwc lowered pressure to manufacture specs at 1.49inwc