for Columbus, OH
Call Staff Is Very Nice
Amirault - Columbus, OH
Kean - Columbus, OH
AC died and I was afraid of large bill or wait. Next day they Carmen out, after confirming arrival time, and I had cool are after a minor service
Jill - Columbus, OH
They were here on a Sunday and fixed the AC . They gave us a great quote for a new unit!!
Great service and quick!
Jennifer - Columbus, OH
Very thorough and honest
Tina - Columbus, OH
Recently had a coolant leak, they were very thorough and honest, got is air before the extreme heat.
Lagana - Columbus, OH
Quinn - Columbus, OH
Great service and fair prices
I like HaDar (idk how to spell it but)
Challacombe - Columbus, OH
another 5 star experience, love working with this company and the people who work here
Angela Yinger - Columbus, OH
James - Columbus, OH
On time and corrected problem
Upon arrival found the 2003 Rheem furnace not operational, Was showing led code 4 with a 2 second pause, pressure switch stuck closed, Took hose off and got switch to reopen, system kicked on operational normal, Pressure switch is intermittent, inducer is pulling enough inwc , Quoting a pressure switch, customer isn’t interested at this time, System operational at departure.
I am Performing our Five Star Tune-Up & Safety Check on a Gas Furnace. All readings were within manufacturer's specifications, unit operating properly at this time.
Upon arrival performed combustion test on furnace and the General Electric furnace failed the test, had over 470ppm from the left tube on the exchanger and 50ppm on the one on right, shut gas valve off and made maintenance supervisor Rex aware, they will be replacing furnace soon, System not operational at departure.
Furnace circuit board issues.
Upon arrival furnace was not operational, Showing led code for low heat pressure switch did not close, Removed exhaust pipe and cycled furnace kicked on operational normal, Took 450psi blower to exhaust and blew it out , Secured pipes and cycled furnace, kicked on operational normal ran for a few minutes in low heat then high heat with no faults or errors, System operational at departure.